Add: 2Floor, Building A, Huilongda Industrial Park, Shuitian Community, Shiyan Street, Bao'an District, Shenzhen City, Guangdong Province, China
Tel: 0086 - 755 - 83570641
Fax: 0086 - 755 - 83570649
Rack mounted patch panel drawer type JFOPP-R&D144 Specification
JFOPT rack mounted patch panel is designed for fiber connection and distribution of backbone fiber cable; it is suitable for fiber splicing, storage and protection. Their standard 19” width make them compatible to standard optical distribution frame with 19” width. And it also can be used alone.
The shell is high intensified & insulated material, thus having excellent mechanic performance
Fiber input: 4
Adapters output: 144core
Suitable for different adapter (SC simplex, SC duplex, LC duplex, ST simplex, FC simplex)
The slide out style can be with changeable adapter plate, 4ports and 8 ports are available.
A completed patch panel will be with adapter, pigtail and accessories like fiber tray, fiber winding wheel, protection sleeve, nylon tie, and snake like tube. Please confirm which type if you want adapter and pigtail with the patch panel.
The slide out and rotate out type is flexible on open and convenient for operations.
Accessories like fiber tray, fiber winding wheel, protection sleeve, nylon tie, and snake like tube can be ordered separately.
Cable input is with rubber dust cover.
The cable entries are big enough for most of cable with different diameters
Standard width make them can be applied to extensive field
Strength core and shell was insulated
Reliable fiber lead and perfect fix up
Reliable pigtail fixes up and perfect protection
Flexible design and enough space make them convenient for operations and maintenance
The surface is spray-painted and the metal part is well protected.
The incision of metal part is well processed and avoids burr and sharp edge.
Technical Data :
Sheet Metal Thickness: Cover =1.2mm, Bottom plate=1.5mm
Operating Temperature: -40℃～+80℃
Operating Humidity: ≤85％（30℃）
Atmospheric Pressure: 70KPa－106KPa
Insulation resistance≥1000MΩ between grounding system and metal parts of cabinet, testing current: DC 500V
Enduring of high voltage: 15KV (DC) /1min, no penetration, no arcs.