Shenzhen Jiafu Optical Communication Co., Ltd
Add: 2Floor, Building A, Huilongda Industrial Park, Shuitian Community, Shiyan Street, Bao'an District, Shenzhen City, Guangdong Province, China
TEL:0086 - 755 - 83570641
FAX:0086 - 755 - 83570649
Fiber Optic Terminal Box JFOPP-TB06AFD Specification
JFOPT terminal box is designed for wall installation and also suitable other application environment. Its compact size and light weight is ideal for the occasion request small capacity. It is suitable for cable with diameter (Φ) less than 15mm
All property indexes are in accordance with National YD/T814-1996 Standard.
The body makes use of cold rolling steel, and the surface use the technique of dim
blowing plastic and it is with strong adhesive force, artistic and durable.
With adapter output: design of 1-2 cable entrance and 6 ports for SC,
LC, ST and FC D type adapter
Cable entrance and fiber exit are sealed with oil resistance NBR to increase the
flexibility. Users can choose to prick the entrance and exit.
Overlapping fiber-melting tray and separate insulation earth unit make the
disposition of the cores, expanding the capacity and cable-earthen flexible,
convenient and safe.
Technical Data :
Sheet Metal Thickness : 1.0mm
Optical fiber winding radius: ≥40mm
Extra loss of fiber tray: none
Fiber length left in tray: ≥1.6m
Fiber capacity: max 12 or 24 cores
Working temperature: -20 °C~+70°C
Lateral pressure-resistance: 500N
Insulation resistance≥1000MΩ between grounding system and metal parts of cabinet, testing current: DC 500V
Enduring of high voltage: 3000V (DC) /5min, no penetration, no arcs
Peel the cable, take off the outer and inner housing, as well as loose contract tube,and wash off the filling grease, leaving 1.1~1.6m fiber and 20~40mm steel core.
Fix the cable-pressing card and the cable, as well as the cable reinforce steel core
Lead the fiber into the melting and connecting tray, fix heat contract tube and melted tube to one of the connecting fiber. After melting and connecting the fiber move heat contract tube and melted tube and fix the stainless (of quartz) reinforce core stick. Make sure the connecting point is the middle of the housing pipe. Heat the pipe to make the two into one. Put the protected joint into the fiber-laying tray.(One tray can lay 6 cores).
Lay the left fiber in the melting and connecting tray evenly, and fix the winding fiber with nylon ties. Use the trays from the bottom up. After all the fiber has been connected, cover the top layer and fix it.
Position it and use the earth wire in accordance with the project plan
Close the cover. It can be installed on the wall or in horizontal line.